We have a lot of issues with our UV building and design we constantly are getting low water lever alarms and it seems when we get these alarms then we start having troubles with different modules as far as bulbs not coming back on etc. But how do we stop the corrosion on wires it’s not just at the plugs it can be in the middle of a run of wire. And our air lines for the wipers start blue and in about 2 months time they are green and very brittle.
I Imagine that you are in a wastewater treatment plant, is it the case?If so, do you have gas detection system in the room where your UV are? If you have a lot of H2S it may be a reason why you have so much corrosion. Does your ventilation system is working properly?
Yes it is a waste water treatment plant, but we do not have either a gas monitor or ventilation system we just simply have all the windows in the building open and a small fan from tractor supply blowing out. They have came and tested the air but still haven’t heard any talk of a ventilation system being installed. Thanks for your input I guess we need to push to get a system in place.