Hello, we would like to outfit some lift stations with a flow sensor for continuous monitoring. The volume is already estimated by a wastewater function within the
local station and by pumping time. Some sites are also equipped with magnetic flowmeters for outflow (but difficult to estimate a real night flow if water levels vary
considerably.) Any other solutions?
Hello, one method is to install a flowmeter at input in order to determine the actual inflow to the lift station. IJINUS-type level sensors can do this insofar as the
installation conditions of your facility will allow.
I tested the S550 and calculation of flow input and pumped/day/night. This lift station was equipped with a flowmeter to monitor discharge. Well, the flow calculated
by the S500 was identical to the one by the flowmeter.