Do any of your installations have their own power generating or conversion systems?
I am the IT director on the Cote d’Azur for a site equipped with Energid’o. Here is some feedback:
Loop on wastewater treatment plant discharge: ACTIFLO Primary Ph-Ch + MBBR + ACTIFLO Clarification
- Alpha Laval plate-and-frame heat exchangers: despite a good level of effluent on average 16 mg/l suspended solids – 60 mg/ in COD and 12 mg/l in BOD tests;:
Feedback: Build-up on exchanger plates that progressively clog because of biomass containing exopolymers that require backwashing every 2 days + bleaching once a week. We are thinking of replacing the exchangers!
Or else, AO en cours OTV/VE on new WWTP on 06 of 150 0000 redox potential with activated sludge system. Anaerobic digestion with methane byproduct injected throughout the natural gas distribution system.